The settings are made via a 3-pole DIP switch arranged on the side.
The DALI-02EM Controller is used to control lamps with DALI-based coloured light control. Light colour and brightness can be set separately via pushbuttons. The module has an integrated DALI power supply and a relay for reducing the standby power of lamps less than 0.5W. It is designed as a lamp installation module with a very small design.
- circadian control (Tunable white) or 2 DALI groups
- DALI broadcast or addressing >> group control
- reduction of the cold white group (only in circadian operation, because cold white LEDs are usually somewhat brighter than warm white LEDs)
Selection of DALI ECGs
We recommend DALI ECGs with a PHYSICAL MINIMUM LEVEL smaller than or equal to 1%. The DALI ECGs are automatically parameterized by the Controller after switching on the operating voltage of the Controller (MIN-LEVEL, MAX-LEVEL, FADE-TIME, POWER-ON-LEVEL, SYSTEM-FAILURE-LEVEL). We assume that the DALI ECGs have implemented and are set to the "DALI standard dimming curve". The Controller can be used to control circadian lamps (warm / cold) or to control two single circuits (setting DIP switch 2). The Controller can be operated in 2 DALI modes (DIP switch 3):
In "broadcast mode" (DIP switch 3 = OFF), addressing of the ECGs is not necessary since the DALI ECGs are addressed in broadcast mode (DALI output 1 = "warm" or channel 1; DALI output 2 = "cold" or channel 2).
In "group mode" (DIP switch 3 = ON) the groups must be set at the used DALI ECGs with an external tool. The LEDs with "warm light colour" or circuit 1 are to be connected to the ECGs with group 0 and the LEDs with "cold light colour" or circuit 2 are to be connected to the ECGs with group 1. Both groups are output at both DALI outputs. Thus 32 ECGs can be connected in total.
To reduce the standby current of the system, the relay can be connected. The relay switches on as soon as at least one of the two DALI outputs or one of the DALI groups is switched on. It is switched off when both DALI outputs or both DALI groups are switched off for at least 30 seconds.
|Operating voltage||198V-264V AC / 175V-280V DC|
|Power consumption||Less than 0.5W at 230V AC|
|Power switching contact||230V AC, max. 1000VA|
|Button input||230V, max. 10mA; typical 5mA|
|DALI interface||Max. 16 DALI ECGs per DALI output (total 32)|
|Connection||Plug-in terminal 0.5-1.5mm² rigid/flexible (8mm stripped)|
|Max. ambient temperature||-20°C to +65°C|
|Typical Tc point (max.)||+70°C|
|Storage temperature||-25°C to +70°C|
|Humidity||1...95% r. h. non-condensing|
>50000h at Tc 70°C|
>100000h at Tc 65°C
|DIP 1||No reduction of the cold light circuit||Reduction of the cold light circuit by approx. 12%|
(only active in circadian mode, DIP 2 ON)
(button function mode)
for controlling circadian lamps (warm white/cold white)
|Single circuit mode|
for controlling 2 single circuits
- warm at DALI output 1
- cold at DALI output 2
|Group mode (DALI addressable)|
Output G0 and G1 at both DALI outputs
- warm (DALI group 0)
- cold (DALI group 1)
The DALI groups on the DALI ECGs must be set using an external tool!!!!
|1||Connection pushbutton input 230V AC L (phase) for colour temperature control|
|2||Connection pushbutton input 230V AC L (phase) for brightness control|
|3||Connection neutral conductor supply voltage 230V AC/DC|
|4||Connection L supply voltage 230V AC/DC|
|5||Connection switching output supply voltage for DALI ECGs (option)|
|PE||PE via housing attachment|
|6||DALI signal for ECG light colour cold white or output DALI group 0/1|
|7||DALI signal for ECG light colour cold white or output DALI group 0/1|
|8||DALI signal for ECG light colour warm white or output DALI group 0/1|
|9||DALI signal for ECG light colour warm white or output DALI group 0/1|
Article no.: 80100150
DALI Compact Light Controller for connecting 2x16 DALI ECGs with single or circadian (tunable white) control by pressing a button.
kostenlose Anfrage / free request
from 1 € 0.00 € 0.00 Incl. 0.00% VAT