Article no.: 80100160
kostenlose Anfrage / free request
from 1 € 0.00 Incl. 0.00% VAT
The DNR-TC Touch Controller is used for convenient operation of the ISYnet DNR system for colour temperature control (HCL).
The functionality is very conveniently managed in an iOS app (see app description). Here you define which functions are assigned to the buttons (on/off, light colour, brightness, manual/auto operation, etc.). The app also provides various switching times, astronomical functions and curve settings.
The DNR Touch Controller only works in conjunction with the DNR-LC DALI Controller and is connected directly to it via a 4-wire line. Up to 3 DNR-TC can be connected in parallel.
Functions (adjustable with iOS-App):
|Operating voltage||24V DC|
|Mounting||flush-mounted box with double frame (GIRA)|
|Connection||pluggable terminal 0.5-0.8mm rigid|
|Max. ambient temperature||-20°C to +65°C|
|Typical Tc point (max.)||+70°C|
|Storage temperature||-25°C to +70°C|
|Humidity||1...95% r. h. non-condensing|
>50000h at Tc 70°C|
>100000h at Tc 65°C
|Design||installation in a standard flush-mounted box with a GIRA double frame (supplied in standard range)|
|Dimensions||HxWxD 127 x 55.6 x 22 mm|
If several Touches (parallel connection up to 3 Touches) are used in the control, the setting is only to be made at Touch 1. All other Touches can be set to default (all 8 DIP switches OFF). Programming the controllers with the smartphone app is only to be made at Touch 1.
|DIP 8||The DEMO mode is switched off (normal operation). The circadian curve is output in 24 h as shown in the app.||The DEMO mode for the circadian curve is switched on. The daily curve (24 h) set in the app is output as a time lapse in 5 minutes (24 h = 5 min).|
|DIP 7||Delivery status: no locking. All possible parameters can be set with the smartphone app.||Locking the parameters "Einstellungen"|
|DIP 6||Locking the parameters "Schaltzeiten" and "circadiane Kurve"|
|DIP 5||Locking the function "Uhrzeit stellen"|
The 4-pole DIP switch on the back is used to configure whether one or more (up to 3) DNR-TC Touch Controllers are operated on the DNR-LC DALI interface.
Article no.: 80100160